Temperature zones may be set in either Fahrenheit or Celsius degrees. The default temperature scale is Fahrenheit. To change to Celsius: 1. Press SENSOR ON/OFF. 2. Press °F / °C. The Model 400 responds: “Degrees Celsius” indicating Celsius scale has replaced Fahrenheit scale. 3. To return to Fahrenheit scale, repeat the key sequence. The Model 400 responds: […]
Articles Tagged: sensaphone
How too adjust voice repetitions in the FGD-0400.
The Voice Repetitions feature of the Sensaphone 400 and 800 allows programming of the number of times the alarm message is repeated per phone call during alarm dial-out. It can be handy to lengthen the number of repetitions if you find yourself having a hard time punching in the acknowledgement code prior to the unit […]
What is my Sensaphone AutoDialer Acknowledgement code?
The default acknowledgement code for a Sensaphone Auto Dialer is 555, if you did not personalize or change the code on installation. Check out all of the Senaphone AutoDialer units at the below links: USA: http://www.absoluteautomation.com/brands/Sensaphone.html CANADA: http://www.absoluteautomation.ca/sensaphone-alarms-s/1867.htm
My Sensaphone 400 constantly reads 150F (65 C), what’s wrong?
The temperature sensor wires are touching or have shorted. Find the short and if possible correct it, if not the replacement SKU is FGD0101.
My Sensaphone 400 constantly reads -20F (-30C), what’s wrong?
The temperature sensor is either disconnected, has broken wires or needs to be replaced. The replacement part SKU is FGD0101.
Can I listen to a demo Sensaphone?
Yes you can! Simply dial – 610-558-4591 – and you will be listening to an actual Sensaphone alarm unit!
What is the maximum length I can run a temperature sensor for a Sensaphone?
This would vary with wire gauges however as a general rule you could run a sensor up to 200 feet with 22AWG wire.